Goodman furnace is equipped with a self-diagnosing electronic control module. In the event a furnace component is not operating properly, the control module LED will flash on and off, depending on the problem encountered. These Goodman furnace error codes can help you locate exact issues to make furnace repairs faster and more cost-effective.
Before you call an HVAC technician, you might have common issues that will be easy to fix yourself. We will show you how to read your Goodman furnace error codes.
The LED lights can be viewed through the observation window in the blower access door. To find the Goodman furnace LED lights, turn off your furnace and remove the front panel. The LED indicator is usually found in the upper right corner of the control board.
The LED will turn itself off for a few seconds before blinking the code once more. Count the number of times that the LED flash before staying off for a few seconds. The number of flashes is your error code.
|Error Code||Potential Problems||What to do|
|Single LED flash, steadily on||Your Goodman furnace has no signal coming from the thermostat and won’t operate.||Check your thermostat for an improper setting or connection.|
|Single LED flash, blinks on and off||Your furnace has locked out due to too many ignition attempts.||After one hour of lockout, your furnace will automatically reset itself.|
|2 LED flashes||The draft blower isn’t functioning properly, or your furnace has a short in the pressure switch circuit.||You should either repair the short or replace the pressure switch.|
|3 LED flashes||Your furnace has an open pressure switch circuit or the induced draft blower is operating when it shouldn’t be.||Check the pressure switch hose for blocks or an improper connection. Otherwise, see if any loose wiring needs tightening.|
|4 LED flashes||Your furnace has a primary open limit circuit.||Check and clean all the filters, tighten the wiring, and see if there are any blockages in the flue.|
|5 LED flashes||Your furnace senses a flame without a call for heat.||Check for a leaky or open gas valve or a lingering burner flame.|
|7 LED flashes||Warns of a low flame sense microamp signal. This is the result of a coated flame sensor or a lazy flame due to poor gas pressure.||Adjust the gas pressure according to the information available to you.|
|8 LED flashes||Your furnace has an igniter circuit problem due to a defective igniter or an improperly connected igniter.||Replace the igniter or check the ground wiring for defects.|
|9 LED flashes||Your furnace has a high-stage pressure switch that won’t close during a high-stage-induced draft blower operation.||Check your Goodman furnace for a pinched or blocked pressure switch hose.|
|Continuous LED flashes||Your furnace has a reversed polarity of 115 volts.||You will have to correct the wiring polarity after reviewing the wiring diagram.|
To prevent property damage, personal injury or death due to electrical shock, disconnect electrical power to the furnace before performing any maintenance.
Resetting Furnace from Lockout
Furnace lockout results when a furnace cannot achieve ignition after three attempts or when it has lost flame five times during a single call for heat. It is characterized by a non-functioning furnace and shown in Goodman furnace error code by 1 LED flashes. If the furnace is in a lockout, it will (or can be) reset in any of the following ways.
- Automatic reset. The integrated control module will automatically reset itself and resume normal operations following a one-hour lockout period.
- Manual power interruption. Interrupt 115-volt power to the furnace for 0 – 20 seconds.
- Manual thermostat cycle. Lower the thermostat, so there is no longer a call for heat for 0 – 20 seconds, then reset to the previous setting.
Continuous LED flashes on Goodman furnace
Furnace must have a 115 VAC power supply properly connected and grounded. Proper polarity must be maintained for correct operation. An interlock switch prevents furnace operation if the blower door is not in place. Keep the blower access door in place except for inspection and maintenance.
When to Call Pro
Goodman furnace should be inspected by a qualified HVAC technician at least once per year. This check should be performed at the beginning of the heating season. This will ensure that all furnace components are in proper working order and that the heating system functions appropriately.
By following these Goodman furnace error codes, you’ll be able to identify and fix the most simple issues with your Goodman furnace. However, it’s more practical to contact a professional HVAC technician for certain tricky problems.